How to Maintain A Dry Type Transformer?Today's first-class dry-type transformer is primarily equipment that relies on air convection to cool. Therefore, it has good heat dissipation performance and excellent environmental applicability. Th...
Dry Type Transformer Cooling MethodThe dry mode of the dry type transformer is divided into natural air cooling (AN) and forced air cooling (AF). In the case of natural air cooling, the transformer can be operated continuously for a lo...
Transformer Megger TestDecember 13, 2017The megger has three terminal posts: one for "L", one for "E" and one for "G" (shield). L is connected to the wires, E is connected to the cable, and the "G" is attached to the insulated paper of the ...view
Three Phase Transformer TestingDecember 13, 2017The no-load test is designed to determine the variable ratio K of the three-phase transformer, the no-load current I0 and the no-load loss P0.The operation steps are as follows: the high voltage side ...view
Voltage Transformer TestingDecember 13, 2017Insulation resistance testing.Requirements: to use 2500V megohmmeter. Compared with initial value and the values over the years, the winding insulation resistance should not change significantly and l...view
Transformer Resistance TestingDecember 13, 2017How to operate the DC resistance tester:1.Power supplyThere are two kinds of power supply supplied by DC resistance tester: AC220V/DC12V. In the case of strong electromagnetic interference, it is advi...view
Dry Type Transformer Testing ProcedureDecember 13, 2017How to shift gears of the dry type transformer:Operation steps:1. Wear insulating boots and gloves.2. Close the air circuit breaker of low-voltage power distribution cabinets step by step.3. Disconnec...view
Electrical Transformer TestingDecember 13, 2017Key points of electrical transformer testing:Rated Capacity (KVA): The capacity to be transported in continuous operation under rated current and rated voltage. Rated Voltage (KV):A o...view
Testing Low Voltage TransformerDecember 13, 2017Insurance Resistance Test of Transformer Low Voltage SideThe digital insulation resistance tester is used to measure the insulation resistance of transformer, motor, cable, reactor, generator and othe...view
High Voltage Transformer Testing ProcedureDecember 13, 2017Firstly, the insulation resistance and absorption ratio of the transformer winding are measured with a high voltage Megohm, and the DC resistance of the winding is measured by a DC resistance rapid te...view
Winding Resistance Test Of TransformerDecember 13, 2017The measurement for the temperature of windingThe temperature in the channel between the high and low pressure winding passages which is measured by dry type transformer is seen as the temperature of ...view
Transformer Testing MethodsDecember 13, 2017Different capacity transformers, different measurement methods, different voltage grades, different core structures and so on, their measurement time is different. If the single phase measurement is d...view
Power Transformer TestingDecember 13, 2017(1) Inspection of transformer power transmission before operationCheck whether all kinds of test documents are complete, whether the primary and secondary leads have the same phase and correct phase c...view